The only difference is SB2WEB24 has a BACnet communication protocol itself.
BACnet is used in larger buildings when multiple systems are to talk together. This could be a duplicate plant and a CTS plant
The advantage of BACnet versus Modbus is that you do not need an address list as you can scan the network and see what is available on the other systems
In homes, you never use BACnet
In principle, yes, you should be sure to observe all respects for wires / cables with other voltages in the board and elsewhere.
When using 0.25mm cable, for example, UTP cable, you should also be aware that all connections are 100% in order to prevent loose connections over time
If you pull a cord or cable with Dupline / Smarthouse bus in pipes with other voltages, the cable / cable must comply with the insulation capability of the 300 / 500V inner conductor.
Pulling the Dupline / Smart-house bus along with other voltages does not interfere with the bus.
We recommend using our special smart-house cord / cable for Smart-House installations.
It has an insulation capacity of 300 / 500V and is therefore approved to pull in tubes with other voltages.
It is 0.5 square solid wire, which ensures better connections
Special colors so it's easier to know and the risk of blending together is reduced
Cable Smarthouse = 200 meter roll with 2 X 0.5 conductors
Cord Pink = 200 meter roll with 1 X 0.5 conductor
Cord Violet = 200 meter roll with 1 X 0.5 conductor
Both controls really the same with DALI, so there's no problem in using a SH2WEB24
When we recommend SB2WEB24 in buildings (offices, schools, sports centers), it is only from later on that you can connect with CTS systems via BACnet
On the SH2WEB24 Controller there is a built-in Web app that works on all platforms, Apple, android, windows phone, pc and Mac
You only type an http: // (controller's ip address) app - for example. http://192.168.1.20/app
Username and password will be added to SH Tools.
We have a quick guide under "Software, Firmware and Manual for Smarthouse" or CLICK HERE